Maintenance & servicing
See how best to maintain your Biodigester and accessories
Learn about our servicing options,
or how to maintain your Biodigester yourself
About our maintenance service
When you purchase one of our Biodigesters or pumping systems, we recommend you book us to carry out essential maintenance and servicing once every 12-18 months.
We'll arrange for one of our experienced team members to inspect your Biodigester at time and date to suit you.
How can I get you to service my Biodigester?
Contact us to arrange your Biodigester service.
View your Biodigester data sheet for servicing recommendations.
Keep your Biodigester running smoothly
Book a service every 12-18 months
The air blower is designed to operate continuously 24 hours a day, but may be operated on a timer system if lightly loaded. The basic recommendations for a 50% loaded ‘T’ Range Biodigester is a continuous cycle of 15 mins on / 15 mins off.
Do not turn off for long periods. The air blower should be checked regularly.
The blowers’ air filter should be checked and cleaned or replaced.
The rubber diaphragms within the air blower should be checked and then replaced every 3 years.
The pipework and fittings within the Biodigester should be checked
Full maintenance instructions are available as a download.
The liquid transfer port and baffle from inner to outer chamber should be checked and cleaned.
The thickness of humus solids crust on the outer chamber should be checked
If an integral pump is fitted it is recommended that a high level alarm is fitted.
This comprises a float incorporating a switch and an externally mounted Xenon flashing beacon to alert of pump failure. These are available from us.
It is the responsibility of the plant owner to ensure that the terms of the “Consent to Discharge” are maintained. Consistent failure to do this can result in legal action.
Alarms are available to indicate failure of the air blower and to indicate high level in the
effluent pump chamber.
A check is required every 12-18 moths.
Where there is a POMA’ pump with orange tube float system this needs to be taken apart and cleaned.
Every month you should check the air blower. It should be checked to ensure that it is not running excessively hot. If it is this may indicate blockage in the air delivery system or that the air filter excessively dirty.
The integral pump should be checked regularly.
The discharge from the outlet should be clear and odourless. If it is not the following may apply:
Emptying may be required
The plant may be overloaded
There may be chemical interference with the process. E.g. hot fat being poured down the drain, excessive use of house hold cleaning chemicals